07 Oct 2022
music fountain is a movable fountain created for entertainment. A system that can control music is added to the fountain. The computer recognizes the audio signal and finally controls the system, so that the light, color and music are perfectly combined, and a three-dimensional picture is generated according to the aesthetic design.
1. The technical equipment of music and cultural fountain control water pump has not stopped development work.
At this time, we need to check and supply the power supply of the main equipment of the water pump of the fountain system: whether the connection structure of the joint is safe and reliable; whether the switch is in direct contact with the society; whether the fuse is blown; whether the three-phase AC power supply is lacking equal. If there is an open circuit, poor contact, blown fuse, or lack of phase, the cause of the problem should be found out and the basic equipment information of the fountain pump should be self-repaired in time.
The second is to check whether the student is the fountain pump operating equipment to realize its own mechanical product failure. Common reasons are: the packing is too tight or the impeller and the pump body are blocked by debris; the pump shaft, bearing, and leakage reduction ring are rusted. ; The pump shaft is severely bent, etc. Exclusion research method: loosen the packing, dredge the water diversion groove; disassemble the pump body to remove sundries and rust; remove the pump shaft for correction or replace it with a new one.
2. The equipment used for the fountain pump of the Conservatory of Music cannot absorb water.
The reason is that there is air in the pump body of the fountain water pump management equipment or gas accumulation in the water inlet pipe, or the bottom valve is not closed tightly, the irrigation water is not satisfied, the vacuum pump packing has serious air leakage, and the gate valve or the flap door is not closed tightly.
Elimination learning method: firstly put the water pressure requirements up, then fill the pump body of the fountain water pump detection equipment with water, and then start the machine. At the same time, it is also to check whether the check valve is scientific and rigorous, and whether there is air leakage in the pipeline and joints. Check that the fountain water pump selection equipment adopts the oil seal ring of the water pump shaft. If the wear is serious, it should be replaced with a new one.
3. Fountain water pump test equipment and facilities supporting service power vehicle motor overheating.
There are four possible reasons for this kind of teaching situation, which need to be checked one by one. On the one hand, it affects the power supply, the second is the ability of Chinese water pumps, the third is to improve the motor data itself, and the fourth is the working and living environment. The specific solutions to these methods can be obtained by yourself according to the consultation and analysis of watershow company.
4. The investment flow resources of fountain pump lifting equipment are insufficient.
This is because: the speed of the power motor of the fountain water pump equipment is not matched or the belt slips, which makes the speed obviously low; the installation angle of the axial flow pump blade of the fountain water pump equipment is too small; the lift is insufficient, the pipeline is too long or the pipeline has right-angle bends; The suction lift of the fountain pump equipment is too high; the bottom valve, pipeline and impeller of the fountain pump equipment are partially blocked by traffic or the impeller is damaged; the water outlet pipe leaks seriously. Eliminate other methods: restore the basic rated speed, remove the belt grease, and adjust the belt tightness; adjust the blade angle to reduce the space where the water pump must be installed in my country, shorten the pipeline or change the curvature of the pipeline; Tighten the packing; remove the network blockage, replace the impeller; replace the leakage reducing ring and block the leaking place.
5. The fountain pump equipment has long-term heating.
Reasons: The bearing is damaged; the clearance of the rolling bearing or the bracket cover is too small; the pump shaft is bent or the two shafts are not concentric; the tape is too tight; thrust to the side. Elimination standard method: replace the bearing; remove the back cover, add a gasket between the bracket and the bearing seat level; investigate the pump shaft or adjust the concentricity of the two shafts; properly adjust the tightness of the tape; add clean butter, butter It accounts for about 60% of the gap in the bearing; removes the blockage in the balance hole.
Multiple scenic spots of the fountain company can use the water features to connect and run through to form an organic scenic spot, thus playing the role of inducing tourists to visit. Waterscapes can also be used to separate a scenic spot to form multiple independent but interconnected and echoing scenic spots, which play a role in improving the viewing value and interest.
Originally published 07 Oct 2022, updated 07 Oct 2022.