As we all know, fountain equipment is mainly composed of water quality, sprinklers, water pumps, underwater lights and so on. Each component has its own unique characteristics and functions. No matter which component fails, it will affect the normal operation of the fountain equipment. What needs to be done for the daily maintenance of fountain equipment?
Water quality guarantee for fountain equipment. The water quality color of fountain equipment shall not exceed 15 degrees, no other colors, and the turbidity shall not exceed 10 degrees, and shall not contain visible objects. The impurity content in the water is not more than 0.1%, the impurity particle size is not more than 0.2mm, the chloride ion content is not more than 400mm/L, and the pH value is within the range of 6.5-8.5. At the same time, we must pay attention to the water recycling of fountain equipment. When the nozzle is required, the circulating water should be filtered.
Check the water pump regularly to eliminate the fault. The problems that often occur in water pumps include no water, less indirect water or water, buzzing when the motor cannot start, low insulation resistance of the motor windings to the ground, etc. The main reasons are that the motor does not start, the pipeline is blocked, the pipeline is broken, and the filter When the network is blocked, the water inlet is out, the electric pump is reversed, and there is foreign matter in the impeller, the cause of the fault should be found first, the fault or blockage should be eliminated, the line should be repaired or the bearing should be replaced, so that the pump can work normally.
The daily maintenance of underwater colored lights is also very important. Underwater colored lights are an integral part of fountain equipment and are easily damaged. Therefore, the daily maintenance of colored lights is also very important. It is best to use heat shrinkable tubes and hot melt to waterproof the colored lights; when assembling the colored lights, ensure that the connection between the colored lights and the lamp holder is firm and not loose; when welding the lamps on the pipes, the lamps must be welded firmly to prevent the lamps from falling off before use It is turned off during the process. After assembly, it should be soaked in 5% salt water for 72 hours. It can be used after the measured resistance value is qualified.